6.6kV - 125kVA Cast Resin Dry Type Transformer , Three Phases , Two
Winding , Power Distribution
1. It can be directly installed at the load center, which is free
of maintenance and install conveniently, therefore it has low
comprehensive running cost.
2. With high moisture resistance, it runs normally at the moisture
and can be put into operation without being dried after outage,
with low loss and local discharge capacity.
3. It has small noise, strong short circuit resistance and
excellent environmental performance, and can run under severe
4. It is safe, fire-retardant, fireproof and environment-friendly.
The hoisting, tooling and testing equipment is complete. Pearl
Electric has passed the ISO9001-2015 international standard quality
management system certification. Adopting advanced technology and
high quality raw material, with first class equipment and strict
processing, SC-series resin casting dry type transformer. All
performance indicators of the products have reached the relevant
national standards and international standards.
Pearl Electric's products are universally used in different
industries, involving power plants, chemicals, construction,
mining, metallurgy, rail transportation and so on. We do utmost to
meet the needs of various users.
Cast Resin Dry Type Transformer, Low Noise, Low Loss and Low Partial Discharge.
|I Basic Information || || |
|1||Rated Voltage ratio||kV||10kV / 0.433 kV|
|1.02||Applicable Standards|| ||IEC 60076|
|1.03||Manufacturer|| ||Pearl Electric|
|1.04||Country of Origin|| ||China|
|II Electric Performance || || |
|2.06||Insullation Class|| ||Class H|
|2.07||Temperature Rise (@40℃ ambient temperature)||K||125K|
|2.08||Cooling Method|| ||AN|
|2.09||Tapping Ranging|| ||±2*2.5%|
|2.1||Vector Group|| ||Dyn11|
|2.14||Load Loss (@120℃)||W||1960|
|2.15||Local Partial discharge||pC||<10PC|
|2.16||Impulse Withstand Voltage (HV/LV)||kV||75/0|
|2.17||Power Frequency Withstand Voltage|
|2.18||Rated Duration of Short Circuit||s||2|
|III Materials & Accessories || || |
|3.01||Core Materials|| ||Silicon Steel Sheet|
|3.02||Winding Materials|| ||Copper conductor/foil|
|3.03||Insulation methods|| ||HV vacuum cast / LV impregnant|
|3.04||Main Insulation Materials|| ||Epoxy Resin|
|3.06||Sensor for Temperature Alarm and Trip||pcs||Yes, contact provided|
- All bushings shall be in porcelain and will be fitted with firm
- The fuse carrying tube should be made of Non conductive and non
breakable materials such as glass fiber and should be fitted with a
provision for lowering and hoisting and fixing into the isolator
base using a fuse carrier extraction rod/stick on a live circuit.
The top of the fuse carrier should be provided with a screw cap to
prevent rain water leakage.
TECHNICAL DATA SHEET
- The supplier shall join to his offer a data sheet including all
characteristics of the proposed cut outs.
- The supplier shall guarantee the equipment to be constructed in
concordance with standard, all materials must be new and not
already used , transformers shall be waterproof.
Tests shall be done in conformity referring to the manufacture
standard as offered in his bid. All tests procedure shall be in
accordance with referring standard.
Design tests (type tests):
A type test report in accordance to referring standard must be
presented with offer. 5-2 Routine test:
All routine tests must be performed by manufacture, results must be
sent to the client before the date of acceptance test (in case of
signature of contract).
The acceptance tests will be held at the factory of the supplier.
The client reserves the right to be represented at these tests.
control on all line isolators.
- Visual examination and verification on all isolators
- Results of routine test examination.
GB/T10228 , GB1094.11 , IEC60076-11 , DIN42523